Wuxi Power Diesel Generator SetWuxi power diesel generator set is manufactured with Wandi diesel engine produced by China large-lot producer Wuxi dynamic engineering company limited, and brand-name supporting generator.
Wuxi Power Diesel Generator SetWuxi power diesel generator set is manufactured with Wandi diesel engine produced by China large-lot producer Wuxi dynamic engineering company limited, and brand-name supporting generator. Wuxi power "Wandi" brand diesel engine has advanced technology, reliable performance and long running time, can stably operate in a variety of environments with easy maintenance and repair.
1. By adopting world's advanced level of HOLSET turbocharger technology and BOSCH high pressure water jet technology, combining with core technology of other internal combustion engines, dynamic performance, economic performance and emission indicators of Wuxi power diesel generator set are significantly optimized and enhanced.
2. Stable performance, high cost performance, economic operation and maintenance costs.
3. Depending on the needs, Wuxi power diesel generator set can be set into different types of products including manual type, automatic type and computer remote control type.
1. Installation locations need to be with good ventilation, generator end should be with adequate air intake, and engine end should be with good air outlet. Outlet size should be 1.5 times larger than tank area.
2.Around installation location should be kept clean and avoid placing objects which can produce acid, alkali and other corrosive gas and steam. If conditional, please configure fire extinguishing device.
3. If used indoors, exhaust pipes must be reached outside, pipe diameter must be larger than silencer pipe diameter and pipe elbows should not be more than 3 in order to ensure smooth smoke evacuation; pipes should be tilted downward with 5--10 degrees to avoid water injection; if exhaust pipe is installed vertically, it must be fitted with rain cover.
4. If construct base with concrete, we need to measure the level with leveling instrument at the time of installation; between generator set and base should be filled with special cushion and anchor bolt.
5. Generator housing must be with a reliable protective grounding; as for generator set asking for neutral-point solid ground, neutral-point earthing must be carried on by professional, and equipped with lightning protection devices; it is forbidden to carry out neutral point grounding directly with main grid grounding device.
6. Generator and two-way switch must be reliable to prevent reverse transmission. Reliability of two-way switch must be approved by the local power supply department.
7. Connecting rod of starter battery must be secure.
|Diesel Model||Generator Mark||